3701-31-04 (C)(2) / pH is within 7.2 to 7.8
Repeat pH was outside the range of 7.2 to 7.8. pH is 7.0 at the time of inspection.
Treat the pool water so that the pH is within the acceptable range.
Facility Type: Pool
[?] Inspection Type: Follow-up
Inspection Date: 28-August-2014
|The following violation(s) have been corrected since the last inspection.|
|3701-31-04 (C)(3)/Total alkalinity is at or greater than 60 ppm|
Total alkalinity was less than 60 ppm. Alkalinity level is 30 ppm at the time of inspection.
Raise the total alkalinity to at least 60 ppm.
|Thank you for correcting the above item.|