3701-31-04 ( D )(6)(a) / ORP reading shall be 650 millivolts or greater.
ORP reading was below 650 mv.
Have the ACC unit inspected to determined why the ORP is low.
3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical Chlorine disinfectant residual was less than 1 ppm for the pool.
Do not operate the pool when the disinfectant residuals are less than what is required. Ensure the chlorine disinfectant residual is at 1 ppm or above prior to placing the pool back into operation.
3701-31-04 (C)(2) / pH is within 7.2 to 7.8
pH was outside the range of 7.2 to 7.8.
Treat the pool water so that the pH is within the acceptable range.
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 23-July-2018
|Please have violations brought into compliance for reinspection. Thank you.|